This section consists of the following:
The U60 DIN 43880 2TE enclosure is 35mm (1.38“) wide, 89.5mm (3.52“) high and 66.5mm (2.62“) deep excluding the network connectors.
Three LEDs are located in the centre of the enclosure. The yellow Service LED on the left (labeled Link or Service), provides a visual indication of the network status of the U60. The RX LED in the middle flashes green when data is received from the network. The TX LED on the right flashes green when data is transmitted onto the network.
The Service status is also provided to the host via the USB interface so that the host can provide a network Service indicator if required.
The U60 FT DIN has a two-way network connector with push clips to retain the network cabling. The network connection is polarity insensitive.
The U60 RS-485 DIN has a three-way network connector, also with push clips to retain the network cabling. The three positions of the connector are used for the following: + (Signal + or B), - (Signal - or A), and SC (Signal Common). When used in unbiased LonWorks RS-485 networks, the network connection is polarity insensitive.
Both the U60 FT DIN and U60 RS-485 DIN also have Micro B female USB connectors for connection to a host processor and come supplied with a suitable USB Type A to Micro-B cable.
The U60 DIN is compatible with the IzoT Router, Windows computers with OpenLDV 5, with hosts communicating with a Layer 5 MIP interface, and with hosts communicating with a Layer 2 MIP interface including hosts implementing the IzoT Device Stack EX.
The Dialog documentation can be useful when using the U60 DIN Network Interface products:
OpenLDV™ Programmer's Guide – describes Dialog's OpenLDV Network Driver and Software Development Kit (SDK)
If you have technical questions that are not answered by the documentation, you can contact Dialog technical support. See https://edgesupport.diasemi.com for more information on Dialog support and training services.